Generally, the temperature of flue gases at the furnace outlet is not measured. Therefore, a special computation procedure is needed to determine it. This paper presents a method for coordination of the numerical model of a pulverised fuel boiler furnace chamber with the measuring data in a situation when CFD calculations are made in regard to the furnace only. This paper recommends the use of the classical 0-dimensional balance model of a boiler, based on the use of measuring data. The average temperature of flue gases at the furnace outlet tk" obtained using the model may be considered as highly reliable. The numerical model has to show the same value of tk" . This paper presents calculations for WR-40 boiler. The CFD model was matched to the 0-dimensional tk" value by means of a selection of the furnace wall emissivity. As a result of CFD modelling, the flue gas temperature and the concentration of CO, CO2, O2 and NOx were obtained at the furnace chamber outlet. The results of numerical modelling of boiler combustion based on volumetric reactions and using the Finite-Rate/Eddy-Dissipation Model are presented.
Dynamic angle measurement (DAM) plays an important role in precision machining, aerospace, military and artificial intelligence. Because of its advantages including high sensitivity, solid state and miniaturization, fibre-optic gyroscope (FOG) has great application prospects in the field of DAM. In this paper, we propose a dynamic angle metrology method based on FOG and a rotary table to evaluate the DAMaccuracy with FOG. The system synchronously collects data from the FOG and rotary table, and analyses the DAM accuracy of the FOG for different sway conditions compared with that of the angle obtained from the rotary table. An angle encoder in the rotary table provides absolute or incremental angular displacement output with angular displacement measurement accuracy of 10′′ (0:0028◦) and angular displacement repeat positioning accuracy of 3′′ (0:00083◦), and can be used as an angle reference. The experimental results show that the DAM accuracy of the FOG is better than 0:0028◦ obtained with the angular encoder, and the absolute DAM accuracy of the FOG is better than 0:0048◦ for given conditions. At the same time, for the multi-path signal synchronization problem in the metrology field, this paper proposes a signal delay measurement method combining test and algorithm procedures, which can control a delay within 25 #22;s.
In this article, we study tilted fiber Bragg gratings (TFBGs) with tilt angles of 6◦ and 8◦, their transmission spectra, and spectral parameters that have a linear dependence on the refractive index of the environment. It is shown that there can be several such characteristics, such as the minimum, width and energy of the spectrum. The linear dependence of the spectrum width on the refractive index does not depend on the tilt angle. The linear dependence of the spectrum minimum is only observed for a tilt angle of 8◦. The results of this work can be used to create a sensor system based on an optical fiber.
Distribution of the exhaust gas temperature within the furnace of a grate boiler greatly depends on its operating parameters such as output. It has a considerably different character than temperature distributions in other types of boilers (with pulverised or fluidised bed), as it varies considerably across the chamber. Results presented in this paper have been obtained through research of a grate-fired hot water boiler with a nominal rating of some 30 MW. Measurements have been taken by introducing temperature sensors into prearranged openings placed in the boiler side walls. Investigation has been carried out for different output levels. Tests involved thermocouples in ceramic coating and aspirated thermocouples. The latter were used to eliminate influence of radiative heat transfer on measured results. Values obtained with both methods have been cross-checked.